NTI's new Temperature/Humidity Sensor with 3-Digit 7-Segment LCD Display adds to their popular line of environment monitoring sensors. The sensor can be used to detect and view real-time temperature or humidity readings, and is compatible with the ENVIROMUX-2D/5D/16D Enterprise Environment Monitoring Systems.
The ENVIROMUX-STHS-LCD supports applications from -4 to 140°F (-20 to 60°C) and 0 to 90% non-condensing relative humidity. It has a temperature accuracy of ±0.72°F (±0.4°C) for 14 to 140°F (-10 to 60°C) and ±0.90°F (±0.5°C) for -4 to 14°F (-20 to -10°C). Humidity accuracy is ±3% at 0 to 80% relative humidity and ±4% at 80 to 90% relative humidity.
The temperature/humidity sensor features a three-digit, seven-segment display with °F, °C and % indicators and a character height of 0.39 in (10mm). The LCD display window has dimensions of 1.10x0.51 inches (28x13mm). Your staff can use the touch-sensitive Mode button on the LCD display to alternate between temperature and humidity readings. A touch sensitive Light button activates an LED backlight for five seconds for a clear view in dark environments.
The Temperature/Humidity Sensor with LCD Display has compact dimensions of 2.7x1.5x4.25 inches (69x38x108 mm) and is wall mountable. Up to 1,000 ft (305 m) of CAT5/5e/6/6a cable (24 AWG) can be connected between the sensor and the ENVIROMUX unit.
Designed for applications where standard patch cables would fail, these exclusive ultra-flexible cable assemblies are rated to 10 million flex-cycles at 1.82" (46.4mm) for continuous motion and automation applications.
The major benefit of using an antenna array over a single Omni directional antenna is that the antenna array provides radiation patterns that a single Omni antenna would not. In most cases, antenna arrays provide greater coverage than a single Omni antenna could.
As our climate becomes more extreme, there is an ever greater need to ensure that your wired and wireless communications equipment can stand up to the elements. If you are thinking about getting stronger protection for your equipment, you may find the following step by step guide useful.